A bi-colour LED on each detector provides a local 360° visible alarm indication. They flash once every minute to indicate that power is on and the detector is working properly. The red LED flashes when the alarm occurs. When there is a fault condition indicating that the detector sensitivity is outside the listed limits or the battery is low, the yellow LED will flash. The alarm can be reset by pressing the button or when the fire alarm is not collected for a long time.
The test button is used to test whether the detector works normally; each time the buzzer is pressed, the buzzer will respond with a drop, while the yellow LED flashes; This button can be used for local silence during fire alarms;Product Features
– High adaptability to the ambient, with dustproof, mothproof,moisture-proof and anti-white light function- Sound & Flash Alarm,low voltage indication,self-test Function
– Manual test,Auto reset Function.
INSTALL THE DETECTOR BASE
A. Open area smoke or heat detectors are intended for mounting on a ceiling or a wall in accordance with the fire standard in your country.
B. Attach mounting base to ceiling or wall.
INSTALL THE DETECTOR HEAD
A. Align detector head alignment mark line with the base’s start alignment mark line.
B. Push the detector head into the base while turning it clockwise to secure it in place.
C. Do not install the detector head until the area is thoroughly cleaned of construction debris, dusts, etc.
D. Test the detector(s) as described in the TESTING section of this manual.
Meets all requirements of latest EN standard